1. All fixtures must be provided with suspension clips at center of fixtures (24″ from both ends).
2. Fixtures are available with optional emergency battery backups. The local design team must coordinate the emergency lighting requirements with the fixture manufacturer.
3. Fixtures must be suspended independently of the ceiling system. The TAF fixtures can not in any way be supported by the ceiling grid or system.
4. The finish of all fixture trims must match the ceiling finish. Coordinate with torsion spring or hook-on ceiling system as required.
QK-BPL-30120EA-WW-R(9006 or white)-0-90
Coordinate fixture mounting with type C-2 and C-5 ceiling systems.
MOD_LFHD14 LED 3000K MOD torsion spring for Hunter Douglas clng system
Modify fixture with 90+ CRI, 3000°k LEDs. Coordinate fixture mounting with C-2 and C-5 ceiling systems.
Supplier: ZumtobelShauna Deland (Zumtobel Project Manager, Client Services) email@example.com Phone: 845.691.7692
Zumtobel Lighting, Inc.
3300 Route 9W
Highland, NY 12528
In addition to the manufacturers listed for each fixture type, the following distributors are approved to assemble complete or partial Audi-approved lighting packages for your project:
Commercial Lighting Industries (CLI)
81161 Indio Boulevard
Indio, CA 92201
P:800-755-0155 x 213
ILLUMINATION RESOURCES INC.
Deborah Witte, CID, MIES, ASID
112 E. Edwards
Ridgeway, IL 62979