1. The local design team must coordinate the fixture mounting accessories with ceiling type and construction and order accessories as required. Fixtures mounted in the torsion clip demountable ceilings require additional mounting clips.
2. The finish of all fixture trims and all visible, non-reflector parts must match the ceiling finish – white in GWB and white panel ceilings and RAL 9006 in perforated aluminum panel ceilings.
3. Fixtures without the option of an integral emergency battery pack should be connected to an inverter to provide emergency lighting where required.
Minimum wall setback 24", maximum wall setback 36", spacing ratio 1.2 x
Supplier: Hubbell Prescolite
Minimum wall setback 36", maximum wall setback 42", spacing ratio 1.0 x
Minimum wall setback 24", maximum wall setback 36", spacing ratio 1.0 x
Supplier: Spectrum Lightinghttp://www.speclight.com/
1. Coordinate mounting
2. Coordinate flange finish
Supplier: ZumtobelShauna Deland (Zumtobel Project Manager, Client Services) firstname.lastname@example.org Phone: 845.691.7692
Zumtobel Lighting, Inc.
3300 Route 9W
Highland, NY 12528
In addition to the manufacturers listed for each fixture type, the following distributors are approved to assemble complete or partial Audi-approved lighting packages for your project:
Commercial Lighting Industries (CLI)
81161 Indio Boulevard
Indio, CA 92201
P:800-755-0155 x 213
ILLUMINATION RESOURCES INC.
Deborah Witte, CID, MIES, ASID
112 E. Edwards
Ridgeway, IL 62979